Bigger is not always better
In addition to its process conditions, the actual flow capacity of a given PRV is driven by the combination of two design elements: the actual orifice area and the coefficient of discharge. Both of these elements are determined by the individual PRV manufacturer’s design and are certified by National Board.
When selecting a valve, one common myth has been the “bigger the flow, the better the valve.”
When a PRV has an exceptionally large orifice area and the discharge is not large enough to accommodate the expanding gas, the outlet can become ‘choked.’ This can lead to built up back pressure which is greater than 10% of the valve’s set pressure. This phenomenon is called “Body Bowl Choking” and it may cause valve instability, exhibited in chatter, flutter or galling on the disc and stem.
There are many reasons why a PRV might chatter, so diagnosing and correcting body bowl choking requires a detailed review of the PRV sizing calculations and consideration of the piping hydraulics, especially the PRV’s back pressure.
Bigger is not always better Potential hardware solutions to correct body bowl choking include restricting the lift (if that option is available) or switching to a balanced design relief valve, such as bellows or pilot operated relief valves.
Tel: 440 838 7560
Published in Valve User Magazine Issue 47
- BiS Valves
- New Tyco 5100 Series Tyco Flow Control Introduces New Series 5100 Pilot-Operated Pressure Relief Valve
- ‘VALVE USERS’ - BEWARE IMITATION PRODUCTS!
- Crane announces new market focused organization
- KKI - STATOIL Frame Agreements
- VALVE USERS - BEWARE BOGUS AGENTS!
- The fuel of the future - Coal?
- Rotork valve actuators specified for southwest China’s first major refinery
- Pressure regulators developed for subsea use Pressure Tech
- ASCO Numatics introduces air operated valves